Enclosure shall be constructed of extruded, anodized aluminum alloy sections to provide a modular surface mounted unit. The Sapphire Series LT system can be manufactured in lengths that range from 1,220 mm to 2,440 mm. Fascia panels, top and bottom cover panels shall be removable to provide access for easy installation and maintenance of the services.
Aluminum strips with High Pressure Laminate (HPL) with three (3) colors to choose from.
Medical Gas Outlets
Amico Corporation manufactures several compatible connection types for Medical Gas and Vacuum Outlets.
Wire for standard and critical branch power circuits shall be #10 or #12 (as specified) type THHN stranded copper wire, 600 volt, with heat resistant thermoplastic insulation for hot (black) and neutral (white). Grounds shall be #10 type R THHN stranded copper wire (green). All ground conductors shall be factory installed in conduit.
Grounding and Bonding
Each power receptacle shall have a ground conductor connected to a grounding screw. A grounding bus will be installed in each device location.
Optional Accessory Rail